Need professional heating and cooling services in East Fishkill, NY? Look no further! Folkes Home Services, Cooling & Burner Service provides expert services from highly trained technicians. We work for your comfort and satisfaction.
Check out our customer reviews below to see examples of our high quality work. Choose Folkes as your HVAC specialist in East Fishkill, NY.
for East Fishkill, NY
Maria - East Fishkill, NY
Greg Murphy he was very professional. Was very thorough analysis as we did have same problem four times in row. I appreciate explanation why it kept happening. His helper was very professional as well.
Kayla - East Fishkill, NY
Kurt was great and he was very professional. I wouldn’t mind having him service my unit again in the future if need be. I have no complaints. 10/10
Arrival to house noticed no power going to unit. Replaced blown fuse. Unit still not coming on due to thermostat uttons frozen not allowing switching options. Replaced thermostat and tested unit and took temperatures of supply and return. Everything operational.
Checked oil level in tank. Tank if full. Tank gauge indicating empty. Ran new oil line in crawl space from tank to furnace and installed check valve at tank. Customer had to leave for work. Still need to return and make connection to furnace and start up system and check operation. Customer will call with credit card payment, could not find check book and was late to work.
Found tiger loop reservoir empty and burner locked out. Reset burner, tiger loop filled and burner fired. Bled a gallon of oil to ensure no air. Still getting small amounts of air up through line. Crawled under home to inspect oil line for holes, splits leaks. Found none. Oil tank is very low. Customer needs to get oil delivery immediately.
Completed installation of tigerloop de aerator system. Purged oil line and cycled system several times. Checked system operation.
Found oil burner off. Primary control lockout. Bled oil line. System has history of oil line being air bound. Recommended installation of tigerloop. Customer has been quoted for work. Customer would like maintenance agreement mailed to her.
Hit reset, bled line, checked electrodes nozzle and burner head, system operational, recommend installing a tiger loop.
Leaned and serviced oil furnace, replaced filter strainer and nozzle.
Was not getting burner to stay on primary showing flame when there was no flame replaced cad cell eye and tested
Clean and service oil with MA that was owed from previous MA, also replaced transformer (Igniter). Mail copy of receipt to customer
Found system little low on r22 added up to 3 pounds and replaced filter also need to clear stuff around floor vents to get better air flow. Also need to replace filter 12x201 every month return is in the laundry room and sucking up all the lint.