Need professional heating and cooling services in Mahopac, NY? Look no further! Folkes Heating, Cooling & Burner Service provides expert services from highly trained technicians. We work for your comfort and satisfaction.
Check out our customer reviews below to see examples of our high quality work. Choose Folkes as your HVAC specialist in Mahopac, NY.
for Mahopac, NY
Rich - Mahopac, NY
I was well informed as to what was needed and how long it would take.
Performed annual maintenance on oil boiler checked all parts and cleaned inside boiler and vent did combustion test kettle leak from relief valve but stops when temp goes down all zones good
Completed annual maintenance on gas boiler. Customer mailed in renewal.
Performed annual maintenance on oil boiler checked all parts and cleaned inside boiler and vent did combustion test skimmed boiler drained returns and tested operation
Completed annual maintenance on oil fired water heater.
1 Gas Renewal
Found oil line air bound. Customer has since had oil delivery. Burner running normally. Checked operation of all three zones. Zone for first floor living room not working. Tried to purge line. No water pressure in zone. Customer had section of baseboard removed by contractor. No heat on living room/kitchen zone. Need to reconnect loop for heat to first floor. Also relief valve on boiler is leaking and also electric water heater leaking from tank.
Found frozen oil lines. Used co2 and push pull on both tanks to clear. Cleared lines checked system operation. Recommended annual maintenance oil water heater used to heat home.
Replaced bad primary control.
Found air handler blower motor overheating and tripping on internal overload. Current running pressures with improperly running blower, 24/156psi, sh 94, sc o/l. While blower is running system pressures are low. System was recently recharged and now low again. Need to set appointment for replacement estimate.
Estimate for ductless in main LR/ kitchen space. James and perhaps wife Liza will be in attendance.
Found fail capacitor. Replaced capacitor, checked system running pressures and temperatures. Customer purchased one year maintenance agreement on ac. Used $50 gift card.
Found failed expansion tank and leaking relief valve. Spoke to owner by phone. He is going to have his home warranty company fix system