Need professional heating and cooling services in Millbrook, NY? Look no further! Folkes Home Services, Cooling & Burner Service provides expert services from highly trained technicians. We work for your comfort and satisfaction.
Check out our customer reviews below to see examples of our high quality work. Choose Folkes as your HVAC specialist in Millbrook, NY.
for Millbrook, NY
He was great
Stefan - Millbrook, NY
Great service, price was a bit high
Karl - Millbrook, NY
The Best Service
Richard - Millbrook, NY
Friendly, work was very clean, explained all repairs.
Professional and efficient
Lon - Millbrook, NY
Service was scheduled to suit my needs. Service was performed in a timely manner. The serviceman answered the few questions I had to my satisfaction. Left the area clean.
Called out for a clogged toilet on the second floor master bathroom. I attempted to clear the trap with the auger with no success. This toilet will need to be replaced as it is not operational. I gave an estimate to replace the toilet and the customer declined and will swap the toilet himself. I replaced the shut off valve to the toilet and drained the tank.
Called out to replace a customer supplied kitchen sink faucet. I removed the old faucet on the first floor and installed a new modem single handle faucet. The water is on and there are no leaks. There is a one year warranty on the installation.
Got error u3 on Mitsubishi thermostat open thermistor wire reset unit and it came on checked pressures and it was little low added 410 A to system it dropped 6 degrees inside and running good at this time when I opened unit there was signs of mice in unit if problem returns we may have to replace the thermistors in the out door unit .this is for the sun room.
Clean and service Oil with MA. Boiler increases to a temp of 200 even though aquastat is set to 170 recommend acid wash on heating coil and have well replaced.
Completed replacement of blower belt. Checked belt tension and airflow to both zones.
System operational, checked wiring, low voltage and high, checked thermostats, control board.
Clean and service Gas
Duct cleaning for 3 systems. 1st system 5 vents, 1 trunk. 2nd system 12 vents, 3 trunks. 3rd system 16 vents 4 trunks
Arrived at curomers home for a leak coming through the Sheetrock in the basement. Found water softener drain line touching up against boiler piping which exceeds 180 degrees at times. Found that over the years a few pin holes where created in line drain line causing a leak when treatment system goes into a regeneration every couple of days. Recommened replacement of line and a piece of insolation to prevent any new leaks. Checked and tested.
Cleaned and serviced gas boiler, renewed MA for 5 air conditioning system and 1 gas boiler.
Remove existing steam hose. Install new 3" steam hose from humidifier location to wine room. Price includes opening up walls needed to route hose to room. Does not include repair of penetrations made in walls.ran 3 inch pipe to wine cellar and tested
Found frozen pipes in room above garage. Broken in 2 spots.
Customer had a shorted fuse on the control board. Replaced it and unit is working.
Performed annual maintenance on oil boiler Checked all parts and did combustion test
Called out for Oder in the water. We recently installed a clarifier water filter and softener. It appears that a valve was closed to the filter and that was the reason the water still retained that sulfur smell. I opened the valve and put the softener in regeneration mode to cleanse the water again. The smell should be greatly reduced once the generation mode stops and the water is drained out of the system. This is under warranty as this likely happened during installation.
Need to follow up with Kikiâ€™s to relocate humidifier
Adjusted dampers and flex in attic need to keep door open to equalize rooms also found expansion tank and relief valve on boiler need to be replaced leaking water
Clean and service Oil, replaced electrodes, air vent, and expansion tank with filtrol valve, tested, purged water lines, system operational.
Replaced reverse osomosis 4 stage filters. Need to be changed once a year
Electrodes were off balance causing system to not to operate, adjusted, tested, system operational.
Connected AC and heat wires tested and all good
Installed two hangers on whole house water filter. Need to get back to install reverse osmosis water filters under island sink in kitchen
Estimate to install sulpher system before water softener removes sulpher also put a 20â€ big blue whole house prefilter.