Need professional heating and cooling services in Millbrook, NY? Look no further! Folkes Heating, Cooling & Burner Service provides expert services from highly trained technicians. We work for your comfort and satisfaction.
Check out our customer reviews below to see examples of our high quality work. Choose Folkes as your HVAC specialist in Millbrook, NY.
for Millbrook, NY
Professional and efficient
Lon - Millbrook, NY
Service was scheduled to suit my needs. Service was performed in a timely manner. The serviceman answered the few questions I had to my satisfaction. Left the area clean.
Installed two hangers on whole house water filter. Need to get back to install reverse osmosis water filters under island sink in kitchen
Estimate to install sulpher system before water softener removes sulpher also put a 20â€ big blue whole house prefilter.
Clean and service Oil with MA, Propane Furnace has bad inducer motor and collector box falling apart recommend to replace.
Arrived at customer home and tested water.sulpher is .05 0 hardness ph normal.also found sulpher sediment in water while running cold water in tub.gave customer estimate to install sulpher system and a sediment pre filter.customer also has water filter under sink in kitchen standard carbon and pre filter.customer said he will get back with us soon.
Clean and service Oil with MA
Completed annual maintenance on oil furnace.
Completed annual maintenance on 5 ac systems. Kitchen system compressor locked out with open internal overload. Tried to cool off compressor could not get overload to reset. Also found boiler locked out on low water pressure fault. Need to order boiler pressure switch, return to repair. Will also need to recheck kitchen condenser when return for boiler repair. Call customer with pricing and availability for repairs.
Found upper rollout switch tripped. Reset and started system. System intermittently locks out on pressure switch opening. Found heat exchanger soot in condensation and on venting. Heat exchanger restriction due to improper venting. Recommended replacement. Jarred to follow up with customer replacement estimate.
Found boiler seals leaking. Chimney base partially blocked, #60 filltrol assembly failed and burner has to be reset intermittently. Recommended system replacement. Need to set appointment for replacement estimate.
AC Tune Up, Found crack drain line recommend to replace.
Did AC check on system unit is 25 years should be replacing it before it stops working.
Did annual AC checks on 6 units full report on all units are on the check sheets
Found evaporator coil partially frozen again. Thawed system and found faulty TXV. Causing low pressure switch to trip and error code on thermostat. Need to order and return to replace.
Checked over system operation of upstairs right side system that was frozen over the weekend. Checked system running pressures and temperatures 112/281, sh 22, sc 12, td 15. Only found restricted air filter on previous service call, which has been changed. System operating normally at this time.
Found upstairs guest room system frozen. Tried to thaw while on site system needs to left of to thaw. Need to return next week to continue diagnostics
Estimate for Ductless Units in his barn.
Juan Carlos A.
A/C tune up
Insufficient Heating,Hydro Air Oil