Need professional heating and cooling services in Millbrook, NY? Look no further! Folkes Heating, Cooling & Burner Service provides expert services from highly trained technicians. We work for your comfort and satisfaction.
Check out our customer reviews below to see examples of our high quality work. Choose Folkes as your HVAC specialist in Millbrook, NY.
for Millbrook, NY
Great service, price was a bit high
Karl - Millbrook, NY
The Best Service
Richard - Millbrook, NY
Friendly, work was very clean, explained all repairs.
Professional and efficient
Lon - Millbrook, NY
Service was scheduled to suit my needs. Service was performed in a timely manner. The serviceman answered the few questions I had to my satisfaction. Left the area clean.
Customer had a shorted fuse on the control board. Replaced it and unit is working.
Performed annual maintenance on oil boiler Checked all parts and did combustion test
Called out for Oder in the water. We recently installed a clarifier water filter and softener. It appears that a valve was closed to the filter and that was the reason the water still retained that sulfur smell. I opened the valve and put the softener in regeneration mode to cleanse the water again. The smell should be greatly reduced once the generation mode stops and the water is drained out of the system. This is under warranty as this likely happened during installation.
Need to follow up with Kikiâ€™s to relocate humidifier
Adjusted dampers and flex in attic need to keep door open to equalize rooms also found expansion tank and relief valve on boiler need to be replaced leaking water
Clean and service Oil, replaced electrodes, air vent, and expansion tank with filtrol valve, tested, purged water lines, system operational.
Replaced reverse osomosis 4 stage filters. Need to be changed once a year
Electrodes were off balance causing system to not to operate, adjusted, tested, system operational.
Connected AC and heat wires tested and all good
Installed two hangers on whole house water filter. Need to get back to install reverse osmosis water filters under island sink in kitchen
Estimate to install sulpher system before water softener removes sulpher also put a 20â€ big blue whole house prefilter.
Clean and service Oil with MA, Propane Furnace has bad inducer motor and collector box falling apart recommend to replace.
Arrived at customer home and tested water.sulpher is .05 0 hardness ph normal.also found sulpher sediment in water while running cold water in tub.gave customer estimate to install sulpher system and a sediment pre filter.customer also has water filter under sink in kitchen standard carbon and pre filter.customer said he will get back with us soon.
Clean and service Oil with MA
Completed annual maintenance on oil furnace.
Completed annual maintenance on 5 ac systems. Kitchen system compressor locked out with open internal overload. Tried to cool off compressor could not get overload to reset. Also found boiler locked out on low water pressure fault. Need to order boiler pressure switch, return to repair. Will also need to recheck kitchen condenser when return for boiler repair. Call customer with pricing and availability for repairs.
Found upper rollout switch tripped. Reset and started system. System intermittently locks out on pressure switch opening. Found heat exchanger soot in condensation and on venting. Heat exchanger restriction due to improper venting. Recommended replacement. Jarred to follow up with customer replacement estimate.
Found boiler seals leaking. Chimney base partially blocked, #60 filltrol assembly failed and burner has to be reset intermittently. Recommended system replacement. Need to set appointment for replacement estimate.
AC Tune Up, Found crack drain line recommend to replace.
Did AC check on system unit is 25 years should be replacing it before it stops working.