Need professional heating and cooling services in Philipstown, NY? Look no further! Folkes Heating, Cooling & Burner Service provides expert services from highly trained technicians. We work for your comfort and satisfaction.
Check out our customer reviews below to see examples of our high quality work. Choose Folkes as your HVAC specialist in Philipstown, NY.
for Philipstown, NY
Roland - Philipstown, NY
service was terrific
Sonya - Philipstown, NY
Kurt F is an excellent service person. He identified the problem and fixed it efficiently showing skill and knowledge. I am very impressed with his expertise.
Found oil burner locked out on primary control, turning off power to nest thermostat. Found air in oil line. Bled line, replaced filter strainer and nozzle. Oil level is low in tank. Told customer to call for delivery. Tested igniter, o.k.. Bill from office.
Completed annual maintenance on on two gas boilers
Replace faucet with different finish from original install.
Pulled pump from initial install found bad splice in wire. Re spliced all connections started and tested. Job complete
Found low voltage Transformer no good on boiler replaced and tested
Returned to install a 80 gallon well tank, submersible pump kitchen sink faucet. Upon arrival I spoke with the home owner and received the alarm code and garage code to access the house. We removed the old kitchen sink faucet, well tank and well pump and installed a 1/2 h well well pump with control box, 80 gallon well tank ad kitchen sink faucet. We let the air out of the water lines and closed the well pit cover. The pressure is at 60 psi and there are no leaks. Here is a 2 year warranty on the well tank and pump and a one year warranty for the kitchen sink faucet.
Called out for low water pressure in the house. Upon arrival I spoke with the customer regarding the well tank and well pump replacement. I checked the the pressure and electric circuit and the well tank is failed. The pump has to be taken out to measure how deep the pump goes into the well. This will be done next week as the home owner will be away.
Zone #3 for unit when you walk into basement circulator was no good also the air vent and gauge replaced all parts and tested left water feeder valve open and drop water temp at the aquastat to 140 think the well is no sensing correct temp and that is why the boiler keeps popping the relief valve
Garage unit got error 6A no ignition I could see the hot surface igniter glow but no light when gas valve open purged gas line and restart unit came on tried a few time it stated up all the time radiant heat for studio was off due to bad circulator replaced and tested
Disconnect two condenser behind garage pumped down system disconnect line and low voltage wires cut line set and taped the ends customer said he would move units when he is ready.
Installed new up bulbs and bulbs still not working. Need to also replace UV ballast. Job not completed.
New UV bulbs donâ€™t match old bulb plugs. Bringing old bulbs back for reference.
Customer stated oil smell coming from boiler. Found one year old boiler running rich. Completed annual maintenance on oil boiler. Set burner with combustion analyzer. Also found incorrect circulator pumps for application.
Customer is looking for an estimate for central air. House was built in 1955 no current system in the home now.
Completed annual maintenance on to ductless ac systems. First floor UV lights are burnt out. Second floor UV lights are lit, but dim. Recommend replacement of UV lights for both systems.
Ac Tune up x5 plus two additional wall units, 3 Split Systems Hydro Air, 2 Outdoor and 4 indoor ductless. Need to call for payment and signatures
Ac Tune up x5 with maintenance Agreement
Install Mitsubishi Heat Pump MXZ-3C30NA heat pump condenser, MSZ-GL09NA Guest Room, MSZ-GL18NA Main Room, linesets, linehide, condensate lines, electric and permits, Customer's electrician to install GFI. Place 18K under desk in office space, 9K under desk in spare room, use 3" PVC to run lineset and condensate to utility room **Exhaust side of condenser to face outside slot wall** #folkes
No AC 2nd Floor, due to system low on R-410a, charged, tested, system operational, added 7lbs 9.8 ounces.
Did annual maintenance on 3 AC system added R22 to fitting room area and capacitor all is good at this time
Manitoga is located in Garrison. It is the site of the mid century modern home and studio for industrial designer, Russel Wright.
Need to return to repair boiler
Replaced OEM Circuit Board in Mitsubishi Mini Split Condenser. Tested and all is good at this time
Estimate for new heating system. Currently has propane. Would like to know his available options.
Referred by Padilla Oil Estimate to install either central A/C or ductless New customer. Bente is the only decision maker.