Need professional heating and cooling services in Poughquag, NY? Look no further! Folkes Heating, Cooling & Burner Service provides expert services from highly trained technicians. We work for your comfort and satisfaction.
Check out our customer reviews below to see examples of our high quality work. Choose Folkes as your HVAC specialist in Poughquag, NY.
for Poughquag, NY
Joe/Theresa - Poughquag, NY
Noah was professional, neat, and explained the entire service to me. Excellent service!
He was so nice and patient. Danny did a fantastic job.
Victoria - Poughquag, NY
Lynne - Poughquag, NY
Eric - Poughquag, NY
Came out when we were in a bind to fix our system. Took the time to review and explain what was happening and how it was going to be fixed with a smile on his face. Made sure we didn’t have any questions and wanted to make sure we were satisfied. With a smile on his face and a pleasant demeanor.
Great crew! In-house??- Not so much
Kimberly - Poughquag, NY
My appt time was btwn 2-4pm. Crew showed up around 5:30. Would have appreciated a call telling me they were running late. Instead, I experienced a rude in-house person argue with me over my slot without apology. She said, “Do you want them to come or not. I can reschedule you.” Whatever happened to customer service and the feeling you actually appreciate our business?? PS If this was strictly based on the two men who came to the door, the score would be “above average”.
Joe - Poughquag, NY
Paul - Poughquag, NY
Very professional, thorough, and knowledgeable. Arrived at 4:59 for a 5:00 appointment. Thank you
Found electrical fault in oil burner primary control. Found water to have gotten into control. Could not find source of leak. Boiler and plumbing above, everything is dry. Replaced primary control and checked system operation. Mail customer invoice.
Need to return for bacteria test.
Cleaned and serviced oil boiler, replaced filter, strainer and nozzle, vacuumed inside and took a combustion and efficiency test.
Customer stated boiler locked out on no ignition error. Started system and took combustion and efficiency test. Found combustion settings incorrect. Too much air. Adjusted to 10% co2, co 168ppm, o2 5.6%. Cycled system serval times with no lockout. Checked incoming gas pressure 12â€w.c. During heating cycle.
Found 2nd Floor zone Valve burnt out, replaced, found zone valve for bonus room on its way out, replaced along side with ball that wasnâ€™t moving, thermostat on 2nd Floor burnt out due to technician, replaced under warranty, no charge, purged water lines, tested all zones, system operational.
Customer tried to take out his blower motor and replace it himself but there was some screws that was not able to be removed I saw some wires not looking good so I tested the blower motor and it was working so we put it all back together and tested the system he has a problem with water coming from his AC so he needs an AC check before starting unit next spring or he would end up in the same problem
Performed annual maintenance on oil furnace checked all parts replaced nozzle strainer oil filter and air filter did combustion test and checked air flow furnace had some water damage from water coming down the chimney customer would keep his eye on it when it rains and primary control should be replaced
Estimate to replaced 29-30 year old oil system. Might like some options on HE systems (such as Buderus) but is open to all input. Anthony is the decision maker.
Clean and service Oil with MA
AC Tune up x2 with MA, both units low on R-410A
MA renewal 1 oil
Boiler Replacement Install Peerless Purefire PF 210 95% direct PVC venting (replace existing piping with all PVC), LWCO, Extrol 30 expansion tank, auto water feeder, backflow preventer, six taco circulator pumps, fully modulating burner, all necessary piping, complete boiler installation, permit filing and closing out, STAIRS, bring faceplate need to replace supply and exhaust with PVC, replace flue Plumbing Perform water test for levels of hardness, iron and manganese, install clear water series 45K grain water softening system, includes all piping and materials needed, 3 year labor warranty from Folkes, first year maintenance visit, includes 10 gallon a minute ultra violet light system and converting iron system into acid neutralizer, replace the emergency shutoff valve for your plumbing fixture. Total;$15732.00 Balance Due:$7866.00
Found expansion tank leaking replaced and tested all zones
Replaced MERV 16 filter. Part of installation.
Arrived at customer home and tested water found hard water at 15 and found low ph.at 5.5 Also found corrosion on valves under faucets.gave customer estimate to install water treatment systems and replace valves under sinks.found no iron ..
Boiler locking out on pressure switch fault code. Found heat exchanger clogged with soot and carbon, igniter and flame sensor rusted and pitted, burner has multiple crack. Customer will be replacing boiler. Office to set appointment for replacement estimate.
Found boiler locked out. Reset boiler and fired. Currently working. Customer will let us know if any problem persists. Need to set appointment for water treatment specialist. Needs to have water tested and is interested in UV light water treatment.
Will receive credit of $725+Tax once warranty id processed & approved.Replaced evaporator coil in attic unit pressure test vacuum system and charged unit all working good at this time #folkes
Boiler was off on reset due to a lot of air in oil line purged oil line and tightened fittings on oil line just got new oil line and tank earlier this year tested and working good at this time
Replaced gauge and vent combo on oil tank also took out quarter bucket of oil till there was no water Dustin to bill
Completed annual check up on ductless heat pump, three zones.
Replace leaking indirect tank with new 40 gallon tank
Found leaking 9 year old bock indirect fired hot water storage tank. Unit is located under stairs. Unit 42â€ tall and 22â€ wide 38 gallon tank 3/4 â€œ water lines. On both domestic and coil side. System sold