Need professional heating and cooling services in Rhinebeck, NY? Look no further! Folkes Heating, Cooling & Burner Service provides expert services from highly trained technicians. We work for your comfort and satisfaction.
Check out our customer reviews below to see examples of our high quality work. Choose Folkes as your HVAC specialist in Rhinebeck, NY.
for Rhinebeck, NY
Found heat pump locked out on short cycle lockout again. Reset system and found that after 20mins high side pressure is getting to 600psi and system cycling on/off on high pressure switch. Checked filter, ductwork and air flow. Spoke to manufacturer rep., system may be overcharged. Removed charge and and put back in factory charge. Also couch in downstairs living room blocking first floor return.
Found heat. Pump locked out on 3 red flash error code. Short cycling lockout. Reset system checked refrigerant pressures, normal. Emergency heat not working either. Found wired incorrectly at thermostat and air handler. Corrected wiring and checked operation. Need to return next Monday for further troubleshooting on heat pump.
Reset condenser, cycled on and off three times, ran for about 10 minutes, system operational.
checked operation of system. Running normally. Noise complaint of loud rattling noise in dining room under unit. Did hear noise once. Sounded like something rattling in supply plenum. Looked into plenum with camera did not see anything, and did not hear noise again after several cycles.
Replacement One 10 Ton R-410A Packaged Heat Pump Unit on back side of main building, York Model #XP120C00R2A1AAA1A, One 12.5 Ton R-410A Packaged Heat Pump Unit on Rooftop of main building, York Model #XP150C00R2A1AAA1A, crane & machinery needed for removal of old & installation of new units, licensed electrician for any necessary electrical work, removal and disposal of old units, all permits required by building department for job ***Removal/re-installation of fence around unit on back of building not included*** Total:$27,980.00 Balance Due:$13990.00
Completed annual maintenance on ductless heat pump with two indoor zones.
New install. Customer stated to warm on second floor. Downflow air handler in second floor closet. No access to ductwork, zoning not an option. Running pressures 126/287, sh 3, sc 16, td 18. 5 degree difference from first to second floor. ECM blower in high speed. Thermostat on first floor. System operating normally.
Completed annual maintenance on Mitsubishi ductless heat pump w/ 3 indoor heads. Customer would like maintenance agreement mailed to him.
Estimate to replace two AC Systems.