Folkes Home Services, Cooling & Burner Service is proud to offer the residents of Carmel Hamlet, NY professional heating and cooling services. Our licensed technicians are dedicated to providing you with 5 star service, every time.
Read our reviews below to see how your neighbors in Carmel Hamlet, NY give us 5 star service ratings. Call us at (845) 896-HEAT (4328) to schedule!
for Carmel Hamlet, NY
Our Reviews by City
Maricel - Carmel Hamlet, NY
I called today and with in a 1 hr a technician was at my house checking out my boiler system. Technician was informative and very professional!! Highly recommend them to anyone.
Joe - Carmel Hamlet, NY
Denise - Carmel Hamlet, NY
Excellent service. Polite and knowledgeable. I'm happy that it is fixed and my kids are warm and toasty again. Thank you
Excellent service! Professional and courteous.
Frank - Carmel Hamlet, NY
Showed up when promised and quickly diagnosed and fixed the problem. Excellent.
Professional and informative.
Joanne - Carmel Hamlet, NY
Larry - Carmel Hamlet, NY
Wonderful service! From original phone call to completed job! Would height recommend,
Joyce - Carmel Hamlet, NY
Donna - Carmel Hamlet, NY
Good..part replaced and we have heat
Glenda - Carmel Hamlet, NY
Antonio Bustamante - Carmel Hamlet, NY
Very professional technician
Dave - Carmel Hamlet, NY
Our gas burner is in the attic in a tight spot up a ladder then shimmying across ductwork. I can not do this. Greg and his partner were very limber and diligent and diagnosed a serious problem with our system that was an immediate health and safety concern. We discussed various options and the price for the work was very reasonable.
Response from Folkes Heating, Cooling and Burner Service:
We are so happy to have been of service to you. We thank you for choosing us.
Edvige - Carmel Hamlet, NY
Edvige - Carmel Hamlet, NY
Roberta - Carmel Hamlet, NY
Great service speedy response
Kevin - Carmel Hamlet, NY
Paul - Carmel Hamlet, NY
Explained in detail what was going on and suggested resolutions.
Susan - Carmel Hamlet, NY
Very professional. Cleaned all up. Now I have to see if unit is as good as everyone says
Manny - Carmel Hamlet, NY
I do not have any negative opion
No heat due to air in oil line, bled , tested, system operational. System needs maintenance.
Checked operation of air conditioning system. Running pressures are 71/141 R410a, superheat 7, sub cooling 8, temperature differential 20. Zoned system that continuously freezes during cooling season. Found undersized ductwork design and layout. Installed digital air temperature sensor, to prevent coil freezing. Also completed annual maintenance on oil furnace. Found oil burner locked out. Ignition transformer has intermittent spark, recommended replacement.
Customer had a cold, did not want me to get sick so I was not able to go into the home. Checked over the Condensor and tested all components. Replaced weak dual run capacitor. Took standing pressures could not get compressor running due to the weather.
Leak at relief valve, found bad expansion tank and air vent, replaced, also replaced relief valve, tested, system operational. Water feeder valve not building pressure in boiler properly, recommend to replace.
AC Tune Up with Ma
Found blown low voltage fuse in air handler for heat pump system. Replaced customer supplied low voltage fuse. Ran system through heating cycle. Both heat pump and electric strip heaters running normally. Tested contactor relay coil and inspected contacts, o.k.. checked all low voltage connections at air handler, heat pump and thermostat. Cycled system on/off several times. Fuse did not blow while onsite. No shorts found in low voltage at this time. Recommended annual maintenance.
Ac Tune up. Mail copy of invoice to customer
found an issue with the wiring in the primary control. Replaced the primary and fixed the wiring. Unit is operating normally.
No heat Second Floor due to bad control board at hydro Air system, replaced, tested, system operational.
Clean and service Oil
Performed annual maintenance on oil boiler checked all parts and cleaned inside boiler and vent did combustion test checked all zones ,thermostat,expansion tank,air vent ,relief valve, circulator,aquastat replaced oil filter ,nozzle, strainer all running good at this time
Checked over operation of heat pump system. Cooling- running pressures 55/125psi, outdoor ambient 45, temperature differential. Normal pressures and temperatures. Checked operation of heat and cooling. Operating normally at this time.
Cleaned and serviced heat pump unit with MA
Completed annual maintenance on heat pump. Customer purchased one year maintenance agreement.
Completed replacement of blower motor for carrier ductless heat pump cassette. Cycled system and checked operation.
Renew 1 gas 1 ac from outbound
Cleaned and serviced oil boiler.
Cleaned and serviced oil boiler under maintenance agreement.
Found unit giving code for the pressure switch. Found the pressure switch stuck closed. Jumped the pressure switch out and the unit started to work. Replaced the pressure switch with a universal one and it is working properly. Tested multiple times.
Completed annual maintenance of gas furnace. No problems at this time, system is operating normally.
Completed annual maintenance on oil boiler. Customer renewed maintenance agreement on oil heat and ac.