Folkes Heating, Cooling & Burner Service is proud to offer the residents of Carmel Hamlet, NY professional heating and cooling services. Our licensed technicians are dedicated to providing you with 5 star service, every time.
Read our reviews below to see how your neighbors in Carmel Hamlet, NY give us 5 star service ratings. Call us at 845-896-HEAT (4328) to schedule!
for Carmel Hamlet, NY
Our Reviews by City
Paul - Carmel Hamlet, NY
Explained in detail what was going on and suggested resolutions.
Susan - Carmel Hamlet, NY
Very professional. Cleaned all up. Now I have to see if unit is as good as everyone says
Manny - Carmel Hamlet, NY
I do not have any negative opion
Completed replacement of zoning control panel. Checked operation of all four zones in heating and cooling modes.
Need to replace belt motor with direct drive motor not enough air flow in the house and condenser locking out on low pressure
Customer is looking for an estimate to replace his ac system. He bought the place about 4 years ago and it is all rusted Age unknown. It does not work. 224-227-4745
Did gas furnace check filled out service check list all is good at this time doing contract buy 3 get 4
Wires were stripped at thermostat and touching r and w to turn on the heat
Completed replacement of evaporator coil for first floor condenser. Pressure tested, evacuated and recharged system. Also completed annual maintenance on both ac systems.
Customer is looking for an estimate for an oil boiler. The existing one has a hole in the front of it. Customer is getting other estimates. Husband is a town of kent police officer and she is a bus driver.
Customer stated condenser locked out again last night. Rechecked system running pressures 115/290psi, sc 12, sh 10. System not low on charge. Checked zoning for possible stuck damper. Dampers opening and closing normally at this time. Belt driven blower may not be moving enough air across coil with only one zone open. Ran system for extended period off time with only one zone open, no change in pressures. Installed supply air sensor to prevent possible freezing. System operating normally at this time.
Did AC check on ductless Mitsubishi unit need to follow up on uv light for system all is working good at this time
Found low pressures lockouts on condenser fault code history. System low on charge. Checked all field connections with electronic leak detector. Charged system to proper operating pressures and temperatures. 114/291psi, sh 7, sc 10, td 20
Found water heater control locked out upon arrival. 4 flashes, ECO limit lockout. Reset control and let water heater get up to temperature. Checked water temperature. Exceeding set temp. Need to return to replace water heater gas valve. Also returning to install water treatment system.
Found compressor not starting. Locking out on internal overload. Capacitor tested o.k.. Installed compressor start assistance kit. Compressor still would not start. 16 year old R22 system needs to be replaced. Need to set appointment for comfort advisor for replacement estimate.
Found capacitor no good in condenser for second floor unit replaced and tested all good at this time
Got error p5 on Mitsubishi thermostat drain problem took unit apart and cleaned drain pump tested and put unit back together
Replacement: Install Amana ARUF single stage air handler, Amana ASX13 single stage condenser, MERV 10 air filtration, removal and complete install of equipment, new pad, copper lines, drain pan, float switch, transitional sheet metal, permit included. new lineset, bring faceplate GFI in attic
Estimate for Ductless Units, only have window units now. Both Lou and Barbara will be at the meeting. **Customer indicates he is 1.5 miles from the Kent Schools, he is technically in Kent. (People get confused by the address).
Element on hot water heater no good customer wants to replace 50 gallon electric
Estimate to replace oil system. About 20 years old. New customer. Michael is the decision maker. Go to back door when you get there.