Folkes Heating, Cooling & Burner Service is proud to offer the residents of Carmel Hamlet, NY professional heating and cooling services. Our licensed technicians are dedicated to providing you with 5 star service, every time.
Read our reviews below to see how your neighbors in Carmel Hamlet, NY give us 5 star service ratings. Call us at (845) 896-HEAT (4328) to schedule!
for Carmel Hamlet, NY
Our Reviews by City
Donna - Carmel Hamlet, NY
Good..part replaced and we have heat
Glenda - Carmel Hamlet, NY
Antonio Bustamante - Carmel Hamlet, NY
Very professional technician
Dave - Carmel Hamlet, NY
Our gas burner is in the attic in a tight spot up a ladder then shimmying across ductwork. I can not do this. Greg and his partner were very limber and diligent and diagnosed a serious problem with our system that was an immediate health and safety concern. We discussed various options and the price for the work was very reasonable.
Response from Folkes Heating, Cooling and Burner Service:
We are so happy to have been of service to you. We thank you for choosing us.
Edvige - Carmel Hamlet, NY
Edvige - Carmel Hamlet, NY
Roberta - Carmel Hamlet, NY
Great service speedy response
Kevin - Carmel Hamlet, NY
Paul - Carmel Hamlet, NY
Explained in detail what was going on and suggested resolutions.
Susan - Carmel Hamlet, NY
Very professional. Cleaned all up. Now I have to see if unit is as good as everyone says
Manny - Carmel Hamlet, NY
I do not have any negative opion
Renew 1 gas 1 ac from outbound
Cleaned and serviced oil boiler.
Cleaned and serviced oil boiler under maintenance agreement.
Found unit giving code for the pressure switch. Found the pressure switch stuck closed. Jumped the pressure switch out and the unit started to work. Replaced the pressure switch with a universal one and it is working properly. Tested multiple times.
Completed annual maintenance of gas furnace. No problems at this time, system is operating normally.
Completed annual maintenance on oil boiler. Customer renewed maintenance agreement on oil heat and ac.
Replaced OEM blower motor for carrier mini split air handler. Also replaced blower belt for right side soccer field system. Balance of $635.62, need to call and collect balance. No one on site. Customer would like blower for main entrance restroom air handler replaced. Need to call with pricing and availability.
Performed annual maintenance on oil boiler checked all parts and cleaned inside boiler and vent did combustion test replaced cad cell eye filled with oil customer tried purging oil line and did not turn off bleeder so there was a lot of oil on the floor and in the burner area
Checked mini split ducted system in menâ€™s bath room the blower is making noise need to be replaced also checked out blower on package unit for soccer field adjusted blower noise only when start up need to replace belt and then check noise level after
Found failed oil burner transformer. Replaced transformer and checked system operation. 3 year part and labor warranty on repair. Need to return to complete maintenance on 2 oil boilers.
Clean and service Gas with MA, Customer declined Water test.
Called out to install a 50 gallon electric hot water heater. Upon arrival I spoke to the customer about the installation of the new hot water heater. After approval I removed the old heater and installed a 50 gallon electric water heater. I had to make adjustments because the tank is a bigger than the old tank. The water is at 120 degrees. There are no leaks. Cleaned up and collected payment. There is a one year warranty for installation and a 6 year warranty from the manufacturer.
Found bottom water heater element failed. Need to replace 50 gallon water heater. Schedule for Thursday morning.
Found flame rollout causing rollout switch to trip. Heat exchanger is restricted with soot and pressure switch hoses were never configure for left side discharge so pressure switch never shut down furnace as it should have. Furnace is shut down and unsafe to use. To to schedule comfort advisor to give replacement estimates.
Replace collector box and p trap for furnace tested unit and trap
Performed annual maintenance on oil boiler checked all parts and cleaned inside boiler and vent did combustion test and checked all zones boiler is showing sign of leaking water from the joints on boiler
Went to unit it was operating normal customer said it did not work when she got up in the morning checked inside the unit there is water leaking from the crack on collector box could be causing problem showed customer how to reset unit till we return with collector box
Estimate to replace 24 year old oil boiler. Customer. She is the only decision maker.
Completed annual maintenance on gas furnace
Performed annual maintenance on gas furnace checked all parts and cleaned burners did combustion test and replaced blower capacitor
Completed annual maintenance on gas furnace and gas water heater.