Folkes Heating, Cooling & Burner Service is proud to offer the residents of Clinton Corners, NY professional heating and cooling services. Our licensed technicians are dedicated to providing you with 5 star service, every time.
Read our reviews below to see how your neighbors in Clinton Corners, NY give us 5 star service ratings. Call us at 845-896-HEAT (4328) to schedule!
for Clinton Corners, NY
Our Reviews by City
Really good service. Great guys who fixed the issue well and quickly.
Peter - Clinton Corners, NY
Completed annual maintenance on oil boiler. Customer declined maintenance agreement.
Referred by Rebecca Agosta. Estimate to add A/C to 1400 square foot home. New customer. She is the only decision maker.
Found no airflow to back bedroom register. Ductwork goes under floor. No access to inspect. Home uses combination of electric baseboard, oil furnace and wood stove. Recommended ductless heat pumps as alternative from of heating and cooling. To parts of home. Furnace serviced by oil company last month. Office to run credit card.
Found water feeder no putting water into the boiler and gauge is stuck at 13 also relief valve leaking replaced all parts and air vent tested all zones all working good at this time
Serviced two A/C units, replaced upstairs filter, cleaned downstairs filters off. Checked all pressures and cleaned all coils. Took amp readings on all units. All readings and the condition of the units look good
No heat due to bad firematic valve cutting off fuel supply to furnace, replaced, tested, system operational.
Found blower not energizing. Electrical fault in air handler control board. Replaced board and checked system operation.
Referred by a friend of a friend Estimate to install new ductless system New customer. She is the decision maker.
Found main first floor system low on charge. Recharged system and injected UV dye into system. Recommended to have UV leak search done this season. Customer will call when he is ready.
Found breaker tripped for condenser. Melted and damages wiring at compressor terminals. Replaced all compressor wiring with compressor terminal rebuild kit. Started system and checked operation. Found second floor system low on charge. Recharged system with R22 and checked running pressures and temperatures. Found cracked drain pan for first floor system. Need to follow up with customer with pricing and availability to replace drain pan. Need to change address to 331 Market La
Juan Carlos A.
Juan Carlos A.