Folkes Heating, Cooling & Burner Service is proud to offer the residents of Cold Spring, NY professional heating and cooling services. Our licensed technicians are dedicated to providing you with 5 star service, every time.
Read our reviews below to see how your neighbors in Cold Spring, NY give us 5 star service ratings. Call us at (845) 896-HEAT (4328) to schedule!
for Cold Spring, NY
Our Reviews by City
Rebecca - Cold Spring, NY
Danny is very professional and knowledgeable, but due to the timing of our problem occurring in the weekend was not able to resolve it. $138 seems pretty steep for an unresolved issue, so we hope we will not incur additional fees.
Completed annual maintenance on oil boiler. Found backflow preventer valve dripping. Replaced and checked operation. Need to set appointment for plumber. Has leaking domestic water valve, canâ€™t get whole house water filter apart and needs a water test for water treatment system.
Completed annual maintenance on oil steam boiler. Customer had renewed maintenance agreement in December.
1 oil renew
Clean and service Oil with MA
Found communicating errors on indoors units. Has indoor units set to auto not to heat. Multiple indoor units set to auto will lock system out. Set all or heat and checked system operation. Recommended annual maintenance.
No heat in living room, flashing error code, tried resetting system, still flashing error code, need to return and troubleshoot with tech support.
Found call for heat from thermostat but primary control not energizing burner and locking out after 45 seconds. Saw this occur twice. Replaced primary control and checked system operation. Boiler is old and in poor condition recommended replacement. Customer wants one mote year before replacing.
Pressed the reset button on the unit and the burner fired. Tested a couple times and it continued to work.
Found one zone airbound. Purged boiler and checked operation.
Completed annual maintenance on oil boiler
Install bypass humidifier model he200a100
Performed annual maintenance on oil checked all parts and cleaned inside boiler and vent did combustion test checked antifreeze and it was to +10 degrees told customer and he said he does not want it also had little leak out relief valve but customer did not want to repair tested all zones and circulation of water
Through peerless boiler website. Looking for oil Boiler estimate- commercial unit - Peerless. Manager will be present as well with Ed. Call ed. commercial property no central air
Found system very low on 410A added 6 lb and dye to do leak check 3 indoor units 2 ducted and 1 wall mounted yolk customer we would check what is acceptable and hope we find it and also if it is in the coil it would be an additional charge balance on leak check $821.50 + tax
Showed customer how to use control
Found screw holding exaust damper broke off so it was touching the wheel replace screw and tested all good at this time
Completed annual service on two ductless units with multiple indoor heads. Found mold growth on two indoor units. Dining room and master bedroom
Did annual oil cleaning checked all parts change nozzle filter strainer cleaned inside boiler and did combustion test all good at this time
Did AC annual maintenance on two systems checked all parts and added 410 to second floor unit report sheet filled out
Estimate to add drop to A/C we installed Customer. Jeff and his wife may be present.
Completed annual maintenance on on high efficiency l.p. boiler. Found antifreeze levels too high. Flushed boiler and added 5 gallons of antifreeze. Rechecked levels, 30%, -10F protection. Customer will correct contaminated flue gas issue by removing fresh air intake and drawing fresh air from basement themselves.