Need professional heating and cooling services in Highland, NY? Look no further! Folkes Home Services, Cooling & Burner Service provides expert services from highly trained technicians. We work for your comfort and satisfaction.
Check out our customer reviews below to see examples of our high quality work. Choose Folkes as your HVAC specialist in Highland, NY.
for Highland, NY
Our Reviews by City
Greg is great
Larry - Highland, NY
John - Highland, NY
Linda - Highland, NY
Kurt takes care of my heating and air conditioning systems. Great service! I can always count on Folkes.
Christine - Highland, NY
Danny is fantastic
Found spill switch tripped and pilot out. On going problem with tripping spill switches. One switch failed, will not reset. Furnace next to water, pulling return air 3 ft. from water heater causing negative draft. Recommended having chimney company look at existing flue witch is only 2 ft. Off the ground. Power venter is possible, but difficult installation. Need to return and replace failed pressure switch.
Customer changes her own filter which is located inside the unit. To change the filter she has to take the bottom door off. When put back it seems the door wasnâ€™t making a good contact with the door switch. Secured the door better and the unit is operating properly. Performed gas cleaning with the maintenance agreement, found a weak capacitor. Recommended to replace it. Changed capacitor and unit is operating properly.
Water anyalysis Iron 0 mg/l Hardness 13 to 15 gpg Ph 6.8 Chroline 0 ppm Sulfur 0
Completed annual maintenance on oil boiler. Need to follow up with customer regarding duct work for stove. And need to set appointment for water testing.
Clean and service sooted Boiler, call back Noah, system not adjusted properly at air band and shutter, pump pressure incorrect and, also found wrong size nozzle, corrected, tested, system operational, did combustion test and smoke test.
Completed replacement of 3 way valve for combi boiler. Filled and purged boiler and checked operation. Main ball valve for boiler supply piping cannot be closed need to get pricing for valve replacement and drain installation so boiler can be flushed properly. Customer wants to speak to manager regarding shipping issue before payment.
Called out to install piping on a recently installed 50 gallon natural gas water heater. I installed the proper pipe for the relief valve and also gave an estimate on installing a shower stall in the first floor hallway bathroom.
Found boiler making hot water. Not switching over into heat mode. 3 way valve making buzzing noise during call for heat. Need to get pricing and availability on parts and hotel to replace.
Estimate to add duct work to wood stove. Customer. Dave will be present.
Tripped spill switch, re-lite pilot, tested, system operational.
Cleaned flame sensor, cleared tubing on inducer motor that connects to pressure switch, system operational.
Replaced bad control board on furnace, causing heat to not operate, customer supplied part, tested, system operational. Call to collect payment
Adjusted spill switch and tested system
Completed replacement of evaporator coil drain pan. Pressure tested, evacuated and recharged system. Checked running pressures and temperatures. Need to bill for balance.
Replaced leaking water feeder and tested all good at this time
Found seized blower motor in furnace. Replaced motor and capacitor. Checked system running pressures and temperatures.