Need professional heating and cooling services in Holmes, NY? Look no further! Folkes Home Services, Cooling & Burner Service provides expert services from highly trained technicians. We work for your comfort and satisfaction.
Check out our customer reviews below to see examples of our high quality work. Choose Folkes as your HVAC specialist in Holmes, NY.
for Holmes, NY
Our Reviews by City
Matthew - Holmes, NY
Matthew - Holmes, NY
Technician was very knowledgeable and experienced with the service being provided also very friendly and easy to talk with
Great, fast service, reasonable price
Nicole - Holmes, NY
After calling our usual company about a loud rumbling from our furnace, and being put off until Tuesday, I decided to take advice and give Folkes a try - I’m so glad I did, and so grateful for the fast, efficient service. We signed up for the service plan, a part will be ordered and replaced next week, and the furnace seems to be running much better in the meantime with no noise and no more smell (our furnace is old and Italian - a great furnace but uncommon and nobody keeps parts on hand). I was so grateful for the rapid response, they were here ahead of the promised time, and they couldn’t have been nicer or more professional. It was a great experience, the price was reasonable, and I really couldn’t be happier. Thank you Folkes!
Response from Folkes Heating, Cooling and Burner Service:
Thank you so much for your kind words. Customers like you are the reason we try so hard to provide WOW Service. We appreciate you.
Courteous and competent!
Tina - Holmes, NY
I highly recommend them for your heating and cooling needs!
Spoke to navien and they are sending the flame rod assembly under warranty to be replaced and if problem returns need to check polarity in system
Customer said he got error 004 spoke to tech support and they said it not a very common error code we checked gas pressures ,gas valve ,ground wire to panel,igniter flame sensor adjusted sensor all looked good at this time if problem returns need to walk with igniter
Will receive warranty refund of $2,665.00 once processed and approved, approx 3-5 weeks. RGA# U0202274124
Cleaned and serviced oil boiler, replaced the filter, strainer and nozzle. Brushed and vacuumed inside of the boiler. Everything is operating properly at this time.
Found collector box with two holes so boiler would suck itâ€™s exaust need to call navien to see what is the next step moving forward need to replace boiler
Cleaned and serviced oil boiler, replaced the filter strainer and nozzle. Customer stated the heat would not come on upstairs sometimes and would have to turn the unit off then on again. Found a blower capacitor that was very weak and replaced it. lol her components 8 the attic are working properly. The weak capacitor may not have been starting the blower every time. Also replaced burnt electrodes.
Found boiler not turning on due to loose wire at aquastat repaired and found zone valve for first floor sticking replaced and tested
No heat due to clogged nozzle, replaced, also found oil lines closed due to threaded rings on valves falling off, replaced, system needs maintenance, system operational. Need to call and collect remaining balance of $31.53, approved by DJ
Found oil leak from high pressure nozzle line at oil pump. Took burner apart and dried out oil. Repaired connection and ran burner through several cycles. Did not see any other leaks. Also checked operation of second floor zone valve. Operating normally at this time.
Found oil pump leaking from the seal
Hit reset, system fires up, hit reset about 5-6 times, system fired up every time, waited for system to go through two cycles, system operational.
Replaced Rielo oil burner pump. Completed annual maintenance on oil boiler.
Found burner firing, rumbling, going off on recycle and firing again. Doing this continuously. Found faulty Rielo oil pump which is also leaking. Also found boiler beginning to soot due to improper combustion. Cleaned of retention head and burner is running better temporarily. Need to get pricing and availability on Rielo oil pump and boiler will be cleaned when we return to repair.
Clean and service Oil Boiler, recommend replacing hot water coil on boiler.
No heat or hot water, system completely sooted, needs to be cleaned.
Customer is looking for an estimate for radiant heat in the kitchen and some plumbing work that needs to be done per Jarrett and the customer. Jarrett would like Pat to call him when he is on his way to go over a few things. Customer would also like a radiator installed in the bathroom if possible.
Did AC annual maintenance on two systems second floor unit had some growth inside the air handler installed uvlight to take care of that problem first floor unit has a hole in the drain pan need to get the two units replaced they both are leaking R22 Refrigerant and they are 19 years
First floor system not cooling. System has no refrigerant. R22 system. Needs to be replaced. Need to call customer to schedule appointment with comfort advisor.
Ref per DF Estimate for multiple ductless units. Wife Beth will be there.
Found capacitor no good in Holmes NY. I replaced and tested pressures and amps all good at this time.
Found first and second floor units low on R22 refrigerant add up to 3 pounds in each system need price to replace both systems. Also drain pan for fist floor hydro is leaking water there is a hole in the drain pan both filters were very dirty sec floor 20x25x1 and first floor 20x22x1.
No hot water
Juan Carlos A.