Need professional heating and cooling services in Lagrangeville, NY? Look no further! Folkes Heating, Cooling & Burner Service provides expert services from highly trained technicians. We work for your comfort and satisfaction.
Check out our customer reviews below to see examples of our high quality work. Choose Folkes as your HVAC specialist in Lagrangeville, NY.
for Lagrangeville, NY
Our Reviews by City
Mike - Lagrangeville, NY
Communication with customer excellent
Mini split install
Jean - Lagrangeville, NY
Matt and Anthony did an amazing job. They were very professional, knowledgeable, came when expected and respectful of my home.
John - Lagrangeville, NY
Men are knowledgeable
Very professional , very please from start to finish
Nancy - Lagrangeville, NY
Jane - Lagrangeville, NY
Came when promised, knowledgeable, left written estimate for consideration
No Ac due to system low on R-410A
Customer looking for options for water heater (such as on-demand etc., additional holding tank etc.) Wants to know his options. Mike will be at the meeting.
Checked over operation of older left side studio furnace. Took combustion and efficiency test. Efficiency 85%, stack 397, co2 10.7%, co 37ppm, smoke 0. Checked nozzle size, fan/limit temp settings, blower and over all system operation. System operating normally at this time. Recommended annual maintenance before winter. Customer wants to wait on replacement estimate.
Added 4lbs of Freon r-22, tested, system operation
No AC on 1st Floor system, Unit low on R-22, recommend residential replacement.
Replaced mini uvlight under warranty model TUV-mini-led.
New Install AC Tune Up
No AC due to system completely empty of R-22, recommend residential replacement. Unit holds 6lbs, 14ounces.
HVAC Install see DF for details #folkes
Completed annual maintenance on oil boiler and air conditioning
Install: Install Amana ASPT Multi speed air handler ,
Found second floor condenser not running due to capacitor being bad, replaced with turbo and tested operation.
Found first floor system not turning on. Replaced thermostat and also found system low on refrigerant. Charged system with R22 to proper running pressures and temperatures. Also checked charge on second floor system. Need to call customer regarding water treatment.
Found boiler with relief valve leaking while pressure in boiler at zero, relief valve bad. Replaced and tested operation.
Customer is looking for an estimate for central air. Currently has nothing in the home now. Customers home is approximately 2300 square feet. He would like 2 zones for upstairs downstairs.
Customer stated upstairs bedroom unit was dripping water. Found system in cooling mode and fan on, but vanes closed. Turned unit on/off several times and vanes are opening and closing properly. System draining properly, no water in pan. Blower wheel reasonably clean. Could not replicate problem. Recommended if problem persists to replace vane motor.
Install 2 ductless units 9K BTU living room, 6K BTU in bedroom MXZ-2C20NA Heat pump condenser, MSZ-GL09NA Living room, MSZ-GL06NA bedroom, complete installation, permit included, electrical not required by FOLKES. Total:$8923.00 Balance Due;$3831.00
Ref by Melissa Fernandez Estimate to replace AC.
Showed customer how to use system and close some doors. Also did not get a good delta t added 410 a into system to get it colder tested and all good at this time. Second floor unit.
Replaced 2-16x20 filters paid in full
System working air flow is not good need to zone second floor unit