Need professional heating and cooling services in Lagrangeville, NY? Look no further! Folkes Heating, Cooling & Burner Service provides expert services from highly trained technicians. We work for your comfort and satisfaction.
Check out our customer reviews below to see examples of our high quality work. Choose Folkes as your HVAC specialist in Lagrangeville, NY.
for Lagrangeville, NY
Our Reviews by City
John - Lagrangeville, NY
Mini split install
Jean - Lagrangeville, NY
Matt and Anthony did an amazing job. They were very professional, knowledgeable, came when expected and respectful of my home.
John - Lagrangeville, NY
Men are knowledgeable
Very professional , very please from start to finish
Nancy - Lagrangeville, NY
Jane - Lagrangeville, NY
Came when promised, knowledgeable, left written estimate for consideration
Cleaned and service both oil fired furnaces. Replaced the filter strainer and nozzles, took combustion and efficiency tests on both. All reading looked normal.
Found system not getting hot due to air in the system added 5 gallon antifreeze and purged lines at same time
Performed annual maintenance on oil boiler checked all parts replaced oil filter strainer nozzle did combustion test and filled out all form to submit to customer .
(Jake is our customer at another address). Replacing 6 AC units
Found restricted drain line. Cleared drain and tested with water. Customer declined maintenance agreement.
Arrived at customer home and did a plumbing inspection.customer wants a laundry sink and pump install and repair on laundry line.gave customer estimate to install laundry sink and faucet and pump.customer will call back when ready.customer would like heating tech to come out for estimate for unit heaters in garage.and oil tank relocation.
Found leak comic from packing knot on ball valve on top circulator repaired and tested
Found water seeping through cast body of pump for indirect. Need to order Taco 007E ECM circulator pump
No Ac due to system low on R-410A
Customer looking for options for water heater (such as on-demand etc., additional holding tank etc.) Wants to know his options. Mike will be at the meeting.
Checked over operation of older left side studio furnace. Took combustion and efficiency test. Efficiency 85%, stack 397, co2 10.7%, co 37ppm, smoke 0. Checked nozzle size, fan/limit temp settings, blower and over all system operation. System operating normally at this time. Recommended annual maintenance before winter. Customer wants to wait on replacement estimate.
Added 4lbs of Freon r-22, tested, system operation
No AC on 1st Floor system, Unit low on R-22, recommend residential replacement.
Replaced mini uvlight under warranty model TUV-mini-led.
New Install AC Tune Up
No AC due to system completely empty of R-22, recommend residential replacement. Unit holds 6lbs, 14ounces.
HVAC Install see DF for details #folkes
Completed annual maintenance on oil boiler and air conditioning
Install: Install Amana ASPT Multi speed air handler ,
Found second floor condenser not running due to capacitor being bad, replaced with turbo and tested operation.