Need professional heating and cooling services in Newburgh, NY? Look no further! Folkes Heating, Cooling & Burner Service provides expert services from highly trained technicians. We work for your comfort and satisfaction.
Check out our customer reviews below to see examples of our high quality work. Choose Folkes as your HVAC specialist in Newburgh, NY.
for Newburgh, NY
Our Reviews by City
Joseph - Newburgh, NY
Danny Always surprises me with the level and care he takes with my heating cooling systems. He has to be the best salesman you have. He calls it making recommendations but he's a salesman in service techs clothing. LOL I would like someone to schedule a sales call to talk about installing an electric water heating system. I would like the installation to be done by Danny.
Response from Folkes Heating, Cooling and Burner Service:
We would be happy to do that. Danny is a great guy and we are happy your received WOW service 🙂
Nino/Natale - Newburgh, NY
Performed annual maintenance on oil boiler checked all parts replaced oil filter nozzle strainer did combustion test and cleaned inside boiler and vent filled out service forms to give to customer
Estimate for two gas boiler replacement. Marie Cruz will be on site to let you in (Super). Call her en route (347) 857-5871. Call Muhammed with the pricing.
Found air vent leaking and water not being re fed into system due to water feeder being bad, replaced both components. Also found one boiler drain beginning to leak and pressure gauge for boiler not accurate, replaced. Purged air from system, started and tested operation.
Customer said Condenser cycles out side when the AC is turn on had the same problem last year at the same time could not find a problem at this time
Perform an plumbing inspection.while inspecting customers toilet on first floor shut off found Koehler leaking when flushed found a crack in toilet tank looks like someone tried to repair.gave customer options and estimates.
Will receive warranty refund of $1,030+Tax once warranty is processed and approved. Replaced indirect water heater coil and boiler relief valve. Filled and purged boiler. Checked system operation.
Found zone control valve for indirect storage tank stuck in closed position. Replaced zone valve power head/ball and checked system operation.
System operational, 28 degree delta t, customer would like estimate for residential replacement.
Clean and service Oil with MA, also replaced oil burner motor
Found broken condenser fan blades. Motor bearing is failed and condenser top mounting grill is cracked. Need to get customer estimate for replacement estimate.
Clean and Service Oil Fired Furnace with MA
No ac due to bad capacitor at condenser, replaced, tested, system operational
Customer stated house doesnâ€™t seem to cool properly. Thermostat set for 75 and air temperature is at 75. Checked system running pressures and temperatures. System running normally at this time. Found filter cabinet door off. Resecured and checked. Recommended keeping thermostat set a few degrees lower for a couple of days to see if it is more comfortable for her. Office to mail invoice, customer doesnâ€™t have email.
Customer is looking for an estimate for a ductless heating and cooling system. Currently right now has window ac units. This would be a full install. Customer is also interested in the financing. 522-4909
Clean and service oil, no AC
Clean and service Oil with MA
Add dye, already paid in full, schedule appointment to come back within a month for second part of leak check
Need to order coil, met with rep, went over all details about what is going on with boiler.
Replace control board Inside fan capacitor bad. Replaced both parts system running normally
Replacement Install AMVC8 80% 2 stage gas valve and variable speed, ASX18 seer 3 ton condenser, 2 stage compressor and A coil, duct cleaning included, MERV 16 air filter allergen system, ductwork transitions, add 1 return to 2nd floor, (1) outdoor GFI,disconnect box, (1) thermostat, electric and permits included, lineset and linehide, removal of old equipment,
May need to change indirect water heater,
Changed filters for both 1st Floor and Second Floor system, recommend to have expansion tank and air vent replaced on boiler, pressure on boiler exceeds over 20
First year ac tune up. Checked evaporator, blew out condensate drain and replaced air filter with 1â€ filter. Blower clean and float safety checked. Adjusted damper to both back bedrooms at customer request airflow noisy. Customer satisfied with noise and airflow to both rooms after adjustment. Outside condenser clean, capacitors good, contactor good with temps and pressures good. system running normally.