Need professional heating and cooling services in Newburgh, NY? Look no further! Folkes Heating, Cooling & Burner Service provides expert services from highly trained technicians. We work for your comfort and satisfaction.
Check out our customer reviews below to see examples of our high quality work. Choose Folkes as your HVAC specialist in Newburgh, NY.
for Newburgh, NY
Our Reviews by City
Shereen - Newburgh, NY
The sweetest and kindest representative in this day and age.
Joseph - Newburgh, NY
Danny Always surprises me with the level and care he takes with my heating cooling systems. He has to be the best salesman you have. He calls it making recommendations but he's a salesman in service techs clothing. LOL I would like someone to schedule a sales call to talk about installing an electric water heating system. I would like the installation to be done by Danny.
Response from Folkes Heating, Cooling and Burner Service:
We would be happy to do that. Danny is a great guy and we are happy your received WOW service 🙂
Nino/Natale - Newburgh, NY
Completed replacement for furnace main control board. Completed wiring and checked system operation.
Found main control burnt out. Do not have a replacement on the truck for this unit.
Clean and service Oil with MA
Performed annual maintenance on gas boiler checked all parts and cleaned burners did combustion test and tested circulation
Found no ignition control module locked out â€œout of sequenceâ€ fault. Found pilot lit without call for heat or any power to gas valve. Pilot valve is sticking open and ignition control is locking out furnace. Need to get pricing and availability on replacing commercial furnace gas valve.
No heat due to bad capacitor at blower motor, replaced, tested, system operational.
No heat due to bad power venter, motor seized up, needs to be replaced.
Called out to perform a plumbing inspection. Upon arrival I spoke with the customer regarding the inspection. Also left estimates for a new water softener and house filter. The customer is concerned about an oder coming from the second floor bathroom. This is partly to due to improper vent lines. To remove the toilet and install a new wax ring may also help reduce the Oder.
Arrived at home, turned on furnace and system started normally. Cycled on/off and checked operation. System running normally at this time.
Called out to replace existing lav faucet with 8â€ spread. Upon arrival I spoke with the customer regarding the price to install a customer supplied faucet. We negotiated a price to satisfy the customer. With approval I remove the old faucet that I had to cut out. I then installed a moen customer supplied lav faucet. The dehumidifier that the customer wanted to install was declined by the customer due to price concern. The faucet is operating properly with no leaks. The work done here today is warranties for one year.
Estimate to install ductless systems Customer. New address. Howard will be meeting with you.
Thermostat causing issue, replaced, tested, system operational
Completed replacement of Venturi, indirect air vent and extended venting outside. Adjusted combustion levels. Office to run c.c. for remaining balance.
Found ball valve on return piping for upstairs zone had been left closed from previous work when changing indirect coil. Opened valve checked heating through upstairs zone.
Found broken Venturi causing ignition lockout. Need to order and replace Venturi, air vent for indirect water heater and extend vent away from fresh air intake. Purchased one year maintenance agreement for boiler.
Performed annual maintenance on oil boiler checked all parts replaced oil filter nozzle strainer did combustion test and cleaned inside boiler and vent filled out service forms to give to customer
Estimate for two gas boiler replacement. Marie Cruz will be on site to let you in (Super). Call her en route (347) 857-5871. Call Muhammed with the pricing.
Found air vent leaking and water not being re fed into system due to water feeder being bad, replaced both components. Also found one boiler drain beginning to leak and pressure gauge for boiler not accurate, replaced. Purged air from system, started and tested operation.
Customer said Condenser cycles out side when the AC is turn on had the same problem last year at the same time could not find a problem at this time
Perform an plumbing inspection.while inspecting customers toilet on first floor shut off found Koehler leaking when flushed found a crack in toilet tank looks like someone tried to repair.gave customer options and estimates.
Will receive warranty refund of $1,030+Tax once warranty is processed and approved. Replaced indirect water heater coil and boiler relief valve. Filled and purged boiler. Checked system operation.