Need professional heating and cooling services in Newburgh, NY? Look no further! Folkes Home Services, Cooling & Burner Service provides expert services from highly trained technicians. We work for your comfort and satisfaction.
Check out our customer reviews below to see examples of our high quality work. Choose Folkes as your HVAC specialist in Newburgh, NY.
for Newburgh, NY
Our Reviews by City
Erick - Newburgh, NY
Service was amazing and fast and professional
Great and excellent service
Carlos - Newburgh, NY
Your work mans now how to do the job
Leaking water pipe between well and pressure tank IMMEDIATELY fixed! Awesome!
Revhen - Newburgh, NY
Great service !!!
Flavio - Newburgh, NY
A true professional with excellent troubleshooting skills
Paul - Newburgh, NY
Linda - Newburgh, NY
Kim - Newburgh, NY
Danny my technician was thorough and always ready to explain if additional work needs to be done.
Dean - Newburgh, NY
Shereen - Newburgh, NY
The sweetest and kindest representative in this day and age.
Joseph - Newburgh, NY
Danny Always surprises me with the level and care he takes with my heating cooling systems. He has to be the best salesman you have. He calls it making recommendations but he's a salesman in service techs clothing. LOL I would like someone to schedule a sales call to talk about installing an electric water heating system. I would like the installation to be done by Danny.
Response from Folkes Heating, Cooling and Burner Service:
We would be happy to do that. Danny is a great guy and we are happy your received WOW service 🙂
Nino/Natale - Newburgh, NY
Defective Nozzle causing issue, replaced, tested, system operational.
Installed and tested draft inducer motor. Unit is operating properly.
Found inducer motor not working. Recommended it to be replaced customer would like to hold off on it for now as it does work sometimes. Took down model and serial for future reference when she does want the part.
Clean and service Oil new Install
Clean and service AC X5
Indirect water heater leaking, also found bad circulator pump not moving heated water from boiler properly through coil in indirect tank. Recommend to replace.
Clean and service Oil, recommend fresh air boot
Cleaned and serviced gas furnace included with install. Checked all electrical components and flu piping.
Customer new to house showed her how the hot water works with a hot water coil in the boiler
Clean and service Gas New Install
Cleaned and serviced gas boiler, cleaned flame sensor and igniter, tested unit and took combustion test.
Found system had ran out of oil. Customer had filled tank up with diesel. Reset and burner started. Recently replaced air vent leaking and upper circulator gasket dripping from boiler being off. Quoted customer for repairs. Wants to wait to see if system continues to leak after boiler heats up.
No heat due to bad aquastat, also found boiler pressure at 5 psi, feeder valve wasnâ€™t opening to regulate pressure, replaced, tested, system operational. For 1st Floor Unit.
Called out to replace a 40 gallon power vent natural gas water heater. I removed the old tank and installed the new 40 gallon Bradford white water heater. There are no leaks and the water is 120 degrees. Cleaned up and collected payment. There a six year warranty from the manufacturer and a 2 year warranty for the installation.
Need to replace hot water heater will give deposit of half and balance after we do install
Clean and service with MA, mail copy of invoice to customer
Called out for a clogged main sewer. I snaked the the main sewer from the rear of the house to the front of the clean out. I then flushed and ran the water to test the waste flow. There is currently no signs of a stoppage. It is recommended to replace the cast iron pipe line to pvc to ensure proper waste flow. An estimate was left for the proposed work. Cleaned up and collected payment for today.
Called out for a clogged vanity sink and shower stall. After speaking with the customer regarding the clogged drains I snaked both the shower stall and lav. I reconnected the pipes and ran the water to test. There is no sign of back ups or leaks. Cleaned up and collected payment.
Called out for a main line stoppage. Upon arrival I met the customer and checked the basement for any clean outs that are accessible. I ran the water in the first floor shower stall and the lav also. Both the sink and shower are draining but the toilet isnâ€™t. It appears to be a main line stoppage. The customer wants to reschedule for the proposed work in the estimate. A diagnostic fee was collected.
Completed annual maintenance on high efficiency gas boiler.
Arrived at customers home for water leak by pressure tank. Found male adapter going into tank tee leaking. Replaced male adapter and piece of pipe. Checked for leaks.
Called out for a leak on a toilet. After checking the leak on the basement toilet, I removed the old caulk and inserted toilet shims and resealed the base of the bowl. I flushed several times to test. There is no signs of leaks and the toilet is flushing properly. Cleaned up and collected payment.
Clean and service Gas, recommend residential replacement & chimney cleaning
Called out for a leak under the kitchen sink. After assessing the leak I removed the entire kitchen sink drain. I installed new parts and ran the water to test. There is no sign of leaks at this time. Cleaned up and collected payment. The work done here today has a one year warranty.
Unit shut down by central Hudson found inducer fan no good and roll out switch burned replaced both parts cleaned burners ,inside boiler and around boiler tested all parts and did combustion test all good at this time