Need professional heating and cooling services in Newburgh, NY? Look no further! Folkes Heating, Cooling & Burner Service provides expert services from highly trained technicians. We work for your comfort and satisfaction.
Check out our customer reviews below to see examples of our high quality work. Choose Folkes as your HVAC specialist in Newburgh, NY.
for Newburgh, NY
Our Reviews by City
Clean and service Oil with MA
Add dye, already paid in full, schedule appointment to come back within a month for second part of leak check
Need to order coil, met with rep, went over all details about what is going on with boiler.
Replace control board Inside fan capacitor bad. Replaced both parts system running normally
Replacement Install AMVC8 80% 2 stage gas valve and variable speed, ASX18 seer 3 ton condenser, 2 stage compressor and A coil, duct cleaning included, MERV 16 air filter allergen system, ductwork transitions, add 1 return to 2nd floor, (1) outdoor GFI,disconnect box, (1) thermostat, electric and permits included, lineset and linehide, removal of old equipment,
May need to change indirect water heater,
Changed filters for both 1st Floor and Second Floor system, recommend to have expansion tank and air vent replaced on boiler, pressure on boiler exceeds over 20
First year ac tune up. Checked evaporator, blew out condensate drain and replaced air filter with 1â€ filter. Blower clean and float safety checked. Adjusted damper to both back bedrooms at customer request airflow noisy. Customer satisfied with noise and airflow to both rooms after adjustment. Outside condenser clean, capacitors good, contactor good with temps and pressures good. system running normally.
Main floor is 1950 SF split in 3 zones, living area, 2 bedrooms and separate 1 Bdr apartment plus more zone is well isolated attic about 1000SF Customer interested in all options. Both Stanley and wife Beatrix will be in attendance.
System Low on R-22, needs charge in order to be operational, recommended to replace unit.
Interested in an estimate for a heat pump unit. He and wife Florence will be at the meeting.
Completed replacement of ductless UV bulbs. Checked system operation.
Condenser running high pressures due to exhaust from boiler to close so when boiler comes on it goes off on high pressures need to relocate exhaust pipe
Found failed dual run capacitor for condenser. Replaced capacitor checked system running pressures and temperatures, checked air filter.
Found mini split system that was installed three days ago almost empty of refridgerant. System has a leak from one of the flare connections. Customer not looking to repair at this time.
Found seized condenser fan motor. Replaced condenser fan motor and found system undercharged. Charged system to proper running pressures and temperatures. Spoke to owner regarding system age, condition and outdated refrigerant. We can call and schedule appointment with comfort advisor to give estimate for replacement. Needed to get system running today for tenants.
Showed customer how to operate system with his zoning.
Found system little low on R410a added and tested all good at this time.
Found system freezing. Blower motor in air handler seized. Need to call customer with pricing and availability of motor.
Completed removal of Goodman coil from unused system and installed it in dentist office. Checked drains with water, pressure tested, evacuated and recharged system. Checked pressure and temperatures.