Need professional heating and cooling services in Newburgh, NY? Look no further! Folkes Heating, Cooling & Burner Service provides expert services from highly trained technicians. We work for your comfort and satisfaction.
Check out our customer reviews below to see examples of our high quality work. Choose Folkes as your HVAC specialist in Newburgh, NY.
for Newburgh, NY
Our Reviews by City
Linda - Newburgh, NY
Kim - Newburgh, NY
Danny my technician was thorough and always ready to explain if additional work needs to be done.
Dean - Newburgh, NY
Shereen - Newburgh, NY
The sweetest and kindest representative in this day and age.
Joseph - Newburgh, NY
Danny Always surprises me with the level and care he takes with my heating cooling systems. He has to be the best salesman you have. He calls it making recommendations but he's a salesman in service techs clothing. LOL I would like someone to schedule a sales call to talk about installing an electric water heating system. I would like the installation to be done by Danny.
Response from Folkes Heating, Cooling and Burner Service:
We would be happy to do that. Danny is a great guy and we are happy your received WOW service 🙂
Nino/Natale - Newburgh, NY
Called out for a clogged sink. I snaked the sink 50â€™ and the water is still backing up. I also used a blow bag which was unsuccessful. It appears that there is an excessive amount of grease in the drain line. An estimate was left for the high pressure mini jet or o re-pipe the drain line from the basement under the kitchen sink. The customer will call when ready to proceed with the proposal.
Called out to to diagnose a leak from a oil fired water heater. After inspecting the heater it was determined that the heater must be replaced with a new heater and power burner. The customer will talk with the home ownerâ€™s insurance company s she just moved in a couple months ago. An estimate was left for the customer and she will call when ready.
1 oil renewal
Turned up temp on water heater to level B. Informed customer that the temperature itâ€™s set at is potential burn hazard.
Arrived at customers home found water heater leaking, recommended replacement. Existing tank is a Bradford white 40 gallon natural gas tall. Estimate includes drawing and removal of old tank and installation of new tank. 2 year labor warranty through folks and 6 year manufacturers warranty through Bradford white.
Water had been shut off to water heater. Turned water back on to tank. Leaking from tank. Need to replace 20 gallon electric water heater. Need to follow up with to replace water heater and drain pan.
Found cast iron baseboard leaking from middle section. Needs to replace 15ft. of baseboard. Quoted customer. Will call us with decision.
Clean and service Gas with MA, also replaced capacitor at blower motor on furnace
Clean and service Oil wit MA
Performed gas triple play, recommended to replace the blower capacitor, customer did not want it replaced yet.
Performed triple play and installed customers thermostat.
Found boiler not igniting. Igniter/flame sensor assembly warped and pitted. Replaced igniter assembly and checked system operation. Need to call customer to schedule maintenance appointment.
Completed annual maintenance on on gas furnace
Upon arrival customer stated he hadnâ€™t hear the noise. Cycled system several times and checked operation and for noise. Did not find noise. Customer has scheduled many maintenance in January, is noise persists they will let us know.
Found exaust disconnected and low voltage wire cur to boiler also hose to pressure switch not connected did all of the above repairs and tested could not test zone correctly needed access to apartment
Completed replacement for furnace main control board. Completed wiring and checked system operation.
Found main control burnt out. Do not have a replacement on the truck for this unit.
Clean and service Oil with MA
Performed annual maintenance on gas boiler checked all parts and cleaned burners did combustion test and tested circulation
Found no ignition control module locked out â€œout of sequenceâ€ fault. Found pilot lit without call for heat or any power to gas valve. Pilot valve is sticking open and ignition control is locking out furnace. Need to get pricing and availability on replacing commercial furnace gas valve.