Call Folkes Heating, Cooling & Burner Service at 845-896-HEAT (4328) for all of your home’s heating and cooling needs in Poughkeepsie, NY. You can rely on Folkes for fast and accurate work performed by experienced HVAC professionals.
Read the reviews below to see why our customers are continually satisfied with our work in Poughkeepsie, NY.
for Poughkeepsie, NY
Our Reviews by City
Brij - Poughkeepsie, NY
Debra - Poughkeepsie, NY
Al - Poughkeepsie, NY
Greg was the best. He was knowledgeable and explained what he was doing and what he observed
Great service technician!
Lisa - Poughkeepsie, NY
courteous, efficient, responsive, professional and competitively priced
Arlene - Poughkeepsie, NY
Professional and efficient from start to finish. Kept every appointment and stayed in contact by phone to advise me within 15 to 30 minutes of their arrival. No waiting around for a 5 hour window as to when they would show up. Everyone I dealt with wa efficient, polite and competent. A rarity today. I follow up visit was necessary through no fault of theirs and they were there as soon as I called and quickly and efficiently remedied the problem. Everyone I dealt with was the epitome of customer service.
AC Tune Up
Stephen - Poughkeepsie, NY
Very professional service on unit, best tech in all the years I've used them. Recommend Folkes to all.
Great service & awesome price
John - Poughkeepsie, NY
Great service & also great price
John - Poughkeepsie, NY
Jarrett was very professional, very informative and just an all around nice guy! Explained everything with us about all there products that they have!
Extraordinary Company & Personnel
Cynthia - Poughkeepsie, NY
We finally found a heating/cooling company who actually cares about its customers! They truly go "above & beyond" in trying to assist their customers every need. We have recommended Folkes to people who have inquired about finding a company who actually knows their business and appreciates their customers. We have always had the best experiences with their workforce -- talented and dedicated in every way!
Found low voltage wiring to second floor condenser damaged. Causing electrical short. Transformer burnt out. Repaired wiring and replaced transformer. Installed low voltage fuse to protect new transformer. R22 systems, both in poor condition. Checked refrigerant levels.
Found blower rubbing against side of unit when fan slows down to stop. Adjusted blower for even spacing on each side of unit to prevent rubbing
Parts we received were incorrect. Took pictures and filter information to order correct hardware.
Ac Tune up with MA
Estimate to install new A/C system. Customer. Debra is the decision maker.
Clean and Service Oil fired hot water heater.
Found compressor no good need to replace system
Found burner locked out on primary control. Reset and burner ignited, flame dropped out and locked out again. Customer needs oil delivery. Line may need to be bled, also recommended annual service before heating season. Need to schedule appointment for plumber. Customer has leak from shower drain into basement.
Installed 4x12 floor register and one 3 1/4 x 14 kick plate cover under kitchen sink. Customer looking to find floor cover for old supply register 10x12 picture taken. If we know a place to get one that would be great, balance due $7115.00 for install paid in full today.
Ac tune. Checked evaporator, blew out condensate drain, checked pump, replaced filter with customer supplied filter, emus and pressures good, blower clean, capacitor good and condenser clean, system running normally. Customer will renew ma at time of furnace cleaning.
Checked over operation of 9k BTU Fujitsu. Current running pressures are 148psi, s.h. 1, temp. differential 21. Re-checked leak repair done at outside fittings last year with electronic leak detector. Not leaks detected at this time.
Thermostat has dehumidifying feature turn on, that keeps the unit running, called tech support to see about turning off feature, feature can not be turned off, system operational.
Completed cleaning of Mitsubishi blower wheel and installed UV lighting kit. Office to run c.c. for remaining balance.
Water leak at ac in garage caused by clogged line, cleared, tested, system operational
Completed annual maintenance on ac system.
Adjusted low temp on boiler and showed customer how to use thermostat
Checked refrigerant levels, normal, found delta t at 19 degrees differential, Evaporator Coil was clogged, cleaned, tested, system operational. Also unclogged drain line. Maintenance Agreement for Oil heat and two A/c units
Performed leak check on first floor unit checked evaporator coil ,line set and condenser coil could not see any leak on system ,leak could of been from schrader cores in unit checked pressures and they were good all is good at this time.